Release Firmware 64-chars D8/D9-2-4-65
Features and Bugfixes:
- With a very special BACnet configuration it could happen that the controller reboots.
- During the summer/winter time changeover in combination with NTP, time shifts could occur.
- We have adapted e-mail security to two-factor authentication.
We support the following e-mail providers:
Gmail, Yahoo Mail, Outlook, GMX, Web.de, Mail.de.In order to ensure that e-mail transmission continues to function smoothly in the future, two-factor authentication must be activated for Gmail and Yahoo Mail and an application-specific password must be created. With Outlook, GMX, Web.de and Mail.de no special settings need to be made. We have described this in detail for each of the listed email providers in our system documentation, keyword “email”.
- The correction value of the analog inputs of RCO816E has been improved
- The BTAE option now works correctly with the analog outputs of the RCO816E in the RCO-Web when BACnet is activated.
- On all controllers without web server, the IP Gateway option is now automatically enabled if ModBus TCP is enabled.